- No chemical mixing.
- No electro-chemical cassettes.
- Doses directly into pressurised lines.
- No high concentration solutions.
- No chlorinated by-products.
- No chlorine or excess acid.
- No residual chlorite in chlorine dioxide product stream.
- No storage of chlorine dioxide required.
- No additional booster equipment.
- Chlorine dioxide concentrations of less than 700 mg/litre.
- Instantaneous chlorine dioxide production in dilute solution.
The Cloxide Catalytic range of chlorine dioxide generator systems deliver ultra-pure chlorine dioxide from 100 gms up to 25,000 gms per day.
The system uses:-
Cloxide R - a modified sodium chlorite precursor for the generation of chlorine dioxide
Regenerant S - sulphuric acid for regeneration of the ion-exchange columns. Please note that this product is only used for regeneration and is not involved in the production of chlorine dioxide.
Catalytic Conversion Cartridge - a catalytic granular bed (Pt/Al 2O3) selected for high activity and fast conversion of chlorous acid to chlorine dioxide
The chlorine dioxide output stream is delivered directly via a digital dosing injection system(s) on a proportional basis from either an impulse water meter or flow monitor.
Clearwater ’s Total Management and Service Package ensures that all aspects of operating this chlorine dioxide system are undertaken by trained engineers including maintenance and chemical handling.
Chlorine Dioxide Output Range (gms/day)
Volume of Water Treated per Day at 1.0ppm Chlorine Dioxide
114 to 227
Up to 200
227 to 454
Up to 450
454 to 1135
Up to 1100
1135 to 2270
Up to 2200
2270 to 4540
Up to 4500
4540 to 9080
Up to 9000
Larger models to specification
Up to 22,700
Up to 22,000
|Installation Electrical Requirements |
240V AC 10 Amp 50Hz (110 volt option available)
|Feed Water Quality |
|Maximum TDS |
1,000 mg/litre as calcium carbonate
|Temperature Range |
40˚F to 100˚F (4˚C to 38˚C)
|Incoming Water Pressure |
40 psi to 100 psi (regulator fitted)
|Total Water Hardness |
If the concentration of calcium carbonate is >170mg/litre we will supply a water softener specifically for the generator. for lower concentrations no softener is required.
|Drain for Regenerant |
Must be atmospheric.
Air gap or tundish to prevent syphoning
pH 5.0 to 7.0 (to drain when inlet pH>6.5)
|Generator Size |
Width = 840mm
Depth = 540mm
|Shipping Weight |
|Required Replacements (undertaken under contract by Clearwater trained personnel) |
Conversion cartridge and filters every 2,000 operating hours. Ion exchange resin every two to three years
For full technical and installation details please contact your local Clearwater chlorine dioxide product specialist.